2018, Volume 1, Issue 2
Department of Architecture & Town planning, Faculty of Science of the Earth, University 3 Constantine, Algeria
Previous studies have shown that the glazing is responsible for the most part of the heat gains and losses in the buildings. Glass has been progressively more used in Algeria. In this country, the building sector is the largest energy consumer. It is responsible of more than 41% of the overall energy consumption, with an annual increase rate of 10.8%. Consequently, glazing is an important factor in determining building energy consumption. From the point of view of aesthetics and visual comfort, great glazed surfaces are desirable. However, in semi-
Keywords: Glazing, WWR, energetic performance, overheating, power consumption
In Algeria, the building sector is the largest energy consumer. It is responsible of more than 41% of the overall energy consumption, with an annual increase rate of 10.8% (N.M.E, 2014). Among aspects of energy design, office buildings offer significant possibilities in order to reduce the power consumption and its environmental impact. However, a detailed attention must be given to its outer envelope, because of its transparency. Windows are important in the workplace for both environmental and psychological reasons (Menzies, et Wherrett, 2005).
These building features combine many functions (daylight, thermal comfort, protection against noise, sun, cold and wind, aesthetics, provision of view to the exterior and safety (Tsikaloudaki, Theodosiou, Laskos & Bikas, 2012). Consequently, selecting appropriate windows is important in terms of occupant comfort and energy savings (Haglund, 2015). In terms of heating needs, glazed surfaces contribute positively to the space heating by collecting solar energy (Tsikaloudaki, Theodosiou, Laskos & Bikas, 2012). However, they are the crossing point of significant solar energy which contributes in warming the space and causes summer overheating. This is the effect of its capacity of solar radiation transmission (Binarti, 2009). The cooling needs are usually resolved with the proper design of the outer envelope, in particular, the glazing part (Hilliaho, Mäkital & Lahdensivu, 2015).
The transparency ratio of facades is defined as the window-
Efficient WWR depends on climate conditions. Consequently, each climate needs a proper fenestration design. Binarti (2009) investigated the optimal window area for a classroom in a tropical zone. He found that a window with a WWR of 20% can be considered with regard to energy-
Many other studies investigated the performance of the facade configuration in a considerable number of cities in the world; however, the bulk of research is carried out in moderate, cold climates and hot climates. Little is understood about the performance of large glazed facade in predominantly semi-
There is a great potential for energy savings on air heating and conditioning when using the ideal Window Area (WWR) in offices, depending on orientation and glazing types. Energy efficient window design should limit both cooling and heating demands. The brief addressed by this study was to evaluate internal conditions in an office space that have large glazed area in Constantine city, and to define an efficient window in terms of heating and cooling. This work intends to provide guidance to building designers with regard to the thermal performance of office buildings.
3. Methodology and Description of case Study
The control of the indoor environment and its requirement is important for office buildings in terms of energy. This work presents the results of a post-
3.1 Introduction of Climatic Condition in the Studied Area
The office room studied in this paper is located in an office building representative of contemporary buildings in Algerian country. It is situated in Constantine city at (36°, 17 N and 7°,23'E), 675m altitude. Its climate is characterized by great temperature oscillations, very cold and wet winters (2.6°C is the minimal average temperature,) and hot summers, where average air temperature presents a value of 25.5°C at the hottest month of the year (Figure1).
The average intensity of solar radiation in this city is significant, as it is about 4230 W/m ² / day on a horizontal surface, according to the National agency of weather data (2014). Total solar radiation on a horizontal surface reaches its maximum value of 337 w/h/m ² in July (Figure 2).
3.2 Description of the building Case Study
The ABAM building (Agency of Building Advancement and Management) which is an office building is selected for the case study. It is built in 2010 and located in Constantine. The ABAM building consists of a ground, underground and 4 storeys. Its long axis is oriented in the east west directions. The envelope has large glazing ratios of exterior façade around 40% to 50%. An office space situated in an intermediate floor of this building is selected for the field measurement. The studied office space shown in Figure 3 has a floor area of 16 m² (3.28m wide, 4.87m long and 2.70m high.) and two façades in contact with the exterior. The fenestration areas are identical Double-
4. The in-
As a first step, to deal with the comfort problem, and to analyze the thermal performance of the space and the effect of glazed area on thermal environment, in real conditions, measurements were undertaken in the selected office space, during the hottest month characterized by highest amount of solar radiation. 7 full consecutive days representative of the hot season (from 03 to 10 august) were selected.
A data logger PCE-
4.1 Results and discussion of in situ measurement
The weather over the 7 measurement days was generally hot and sunny. To allow air entering in the space, the windows were fully opened during the occupation hours (from 8:00am to 12 am and from 13pm to 16:30 pm). Since the office space did not have significant thermal storage or conditioning equipment, indoor environmental conditions of this office room followed closely the outdoor conditions with the expected attenuation of temperature extremes. The curves in figure 5 indicate that the outdoor temperature had a maximal diurnal variation of 24°C, from 14°C to 38°C while the simultaneous indoor temperature was varying from 23.2°C to 33.0°C, showing a maximum diurnal variation of about 9.8°C. The average indoor temperature of the space was approximately 2.6 °C higher than the average outdoor air temperature for the measurement period.
The examination of the curves shows that the maximum temperatures in the office room occurred during midday periods, regardless of the solar heat gain and the poor control measures applied. In occupied hours and in addition to dependence of indoor temperature on the amount of solar energy received by the glazed part of the envelope, occupants open the operable window to generate an air movement to improve their comfort. The office room was consequently exposed to a high overheating risk.
The large temperature difference between the two curves is observed in night time period. The external temperatures fall considerably in night time while internal ones remained higher, well above the comfort limit (Tc=25.42°C) calculated for Constantine with Auliciems formula for the hot season in Constantine. It is clear that night ventilation is not envisaged because windows were often left closed, to prevent drafts that may disrupt papers on desks within the office area. As a result, excess heat is accumulated in the space the following day.
The temperature recorded inside the office room is found to be higher than the comfort limit, for 96 % of all measurement period and 100% of occupied hours (figure 6). From the analysis of the above referred literature and the result of the in-
In order to find out the optimal window area in terms of heating and cooling loads, simulation is performed for all year round, using the simulation program 'Pleiades comfie 22.214.171.124'. The office room monitored and described in the first section is selected for simulation. The office room characteristics of building materials are described in table 1, and the simulation results are presented and discussed in this section.
5.1 Simulation variables
There are many parameters in the design of windows in terms of thermal comfort, the most important are:
So, the energy performance of different types of glazing used in buildings in Algeria has been investigated: A one pane glazing, a double glazing and a double glazing with low-
5.2 Occupancy and operation schedules
The internal loads in the office room consisted of the heat generated by one computer (450 W) and 3 peoples (80 W each). The thermostat setting was 27°C for cooling, and 19°C for heating during occupation hours. The ventilation rate was 57 m3/h per Person. Determination of energy loads in the modeled office space, for all cases is given by kilowatt hour/m3.
5.3 Results and discussion
5.3.1. The effect of window-
In order to select the most effective WWR, each glazing type has been varied by a step of 10% in the four principle orientations. It was found that when using a single glazing (type a) in the southern orientation, a WWR of 30% performs better. However, when using a glass (type b) or (type c), the window with more glazing surface in contact with exterior (a window-
The risk of overheating in the Western orientation is avoided because the great amount of solar energy is received out of the occupancy hours. Subsequently the increase of the window area has a positive return on saving energy for heating and has no penalty on cooling energy demand. Therefore, for both heating and cooling loads, energy demand decreases with increasing WWR to 10% in Western orientation. In contrary when using a glazing (type a) in Northern and Eastern orientation, the reduction of window size from 50% to 10% leads to a quick decrease of energy loads by approximately 8%. The decrease of energy loads is less affirmative for the glazing (type b), and (type c) by a ratio of 3%.
5.3.2 The effect of orientation
The building was rotated by 90°. The office room energy use is affected by orientation changes. Simulation results indicate that the orientation is another fundamental variable which can strongly influence the energy savings of the glazed façade, as it may be mounted in the South, West, North or East faces of a building. Results for window use in the four main orientations are shown in Figure 7.
For energy savings where both heating and cooling are concerns, the South face is an efficient direction with total annual heating and cooling loads between 67.25 and 70.33 kWh/m3. This is understandable considering that South orientation receives lower solar energy in hot season. Positioning glazed spaces in the South face can reduce the total energy load, because solar heat gain has a positive effect by increasing the indoor temperature in cold season and reducing it in hot season. Also, in non-
5.3.3 The effect of glazing types
The energy demand for heating and cooling seasons resulting from the use of the three glazing types described above was compared. It has been found that the type of glazing materials used in building construction makes a significant contribution to the annual energy consumption.
In Northern and Eastern orientations, the single Glazing (type a), with the higher U value (5.10 W/m2.°K ) allows heat transferring between inside and outside. Therefore, it is the less efficient in this study, particularly when great WWR is employed in external wall (Figure 8). Total annual heating and cooling loads can reach 78,6 kWh/m3 in the Eastern orientation. The double glazing (type b) is the most promising case. It failed to produce acceptable results. The use of glazing (type b) leads to better energy performance than the other options in all the studied orientations. By minimizing the heat transfer through glazing, it aims at the reduction of the heating demand. While the glazing (type c) allows optimizing solar protection and reducing heat transfer. Its Low emissivity coating and gas fillings are important topics here. It performs better than glazing (type a).
5.3.4 Ideal WWR for the office room model
The findings from investigating the effects of individual parameters (orientation, glazing type, and WWR) have been combined to formulate a glazed façade that has the low heating and cooling loads in constantine. Table 3 indicates optimal combinations of design measures represented by the ideal WWR for all orientations and glazing types. From this table we can see that energy loads increase as the window area increases. Reducing WWR leads in reducing annual energy loads for glazing (type b), and (type c) for Eastern and Northern orientations. The Southern and Western orientations admit a larger WWR (50%) by using a glazing (type a, and b), in fact of their capacity to admit solar thermal gains in cold period. In contrary, in hot season the space is protected from solar rays.
The investigation of an office room located in Constantine city has shown a discomfort and an overheating in a week representative of the hot period. The energy potential of employing glazed facades in office rooms is examined. Design variables such as WWR, glazing types and orientation were evaluated with the assistance of Pleiades comfie program. This analysis defined the most efficient window area (WWR) in an office building, in a semi-
Bektas, B and AKSOY, U.T. 2008. Investigation of the Effects of Orientation and Window Usage on External Walls in Terms of Heating and Cooling Energy Turkish J. Eng. Env. Sci. 32, 23 -
Binarti, F. 2009. Energy-
Eskin, N & Turkmen, H. 2008. Analysis of annual heating and cooling energy requirements for office buildings in different climates in Turkey Energy and Buildings 40 (5) 763-
Haglund, K. Window selection methodologies and optimization in high-
Hilliaho, K., Mäkital, E., and Lahdensivu, J. 2015. Energy saving potential of glazed space: sensitivity analysis. Energy and Buildings. 99, 87-
Inanici, N & Nur Demirbilek, F. 2000. Thermal performance optimization of building aspect ratio and south window size in five cities having different climatic characteristics of Turkey. Building and Environment 35, 41-
Jaber, S & Ajib, S. 2011. Thermal and economic windows design for different climate zones. Energy and Buildings. 43(11) 3208-
Kontoleon, K.J & Bikas, D.K. 2002. Modeling the influence of glazed openings percentage and type of glazing on the thermal zone behavior. Energy and Buildings 34 (4), 389-
Menzies, F & Wherrett, J.R. 2005. Windows in the workplace: examining issues of environmental sustainability and occupant comfort in the selection of multi-
Meteonorm, Meteorological Database, Version 7, Software and Data for Engineers, Planners and Education.
N.A.W.D, 2014. National agency of weather data. ain el bey. http://www.meteo.dz
N.M.E, 2013. Publication of the National Ministry of energy. National Energy Appraisal: Bilan Energétique National. N.M.E. http://www.energy.gov.dz/fr/statistiques.
Tsikaloudak, Ki., Theodosiou, K., Laskos, TH & Bikas, D. 2012. Assessing cooling energy performance of windows for office buildings in the Mediterranean zone, Energy Buildings. 49 (64), 192-
Waheeb, S.A. 2010. Shading Design Guidelines and Reduction of Cooling using Different Glazing Heywood J. Umm Al-
Journal of Buildings and Sustainability -
INSIGHTCORE ® -